Payment & Shipping Terms:
|Product Name::||Customize Pass Box||External Size:||1200*800*1500mm|
|Transfer Window:||6 Pcs||Interlock Structure:||Electronic Interlock Or Mechanical Interlock|
|Material::||Stainless Steel Or Others||MOQ:||1pcs|
dynamic pass box,
air shower pass box
Electronic interlock device: internal use of integrated circuit, electromagnetic lock, control panel, indicator light, etc. to achieve interlocking, when one of the doors is open, the other door open indicator light does not light, telling that the door can not be opened, and the electromagnetic lock The action implements an interlock. When the door is closed, the other electromagnetic lock starts to work and the indicator light illuminates, indicating that the other door can be opened.
1). Electronic chain transfer window.
2). Mechanical chain transfer window.
3). Self-cleaning transfer window transfer window according to the working principle can be divided into air shower transfer window and ordinary transfer window, laminar flow transfer window. Various types of transfer windows can be made according to actual requirements.
4). Optional accessories: walkie-talkie, germicidal lamp and other related functional accessories.
The installation method is edited in a convenient location for the wall, and then the hole is opened. The hole is generally about 10 mm larger than the outer diameter of the transfer window. The transfer window is placed in the wall, generally installed in the middle of the wall, and is balanced and fixed, with rounded corners or other decorations. The strip is used to decorate the gap between the transfer window and the wall, and the glue seal can be modified.
Internal Work Zone
|Cabinet Material||Epoxy powder coated steel / Stainless steel|
|Insider Material||Stainless steel|
|Interlock system||Mechanical Interlock / Electronic Interlock|
Electronic Interlock Or
UV light Power supply
Product and Solution Selection
1. Outer and Inner Dimension. The outer dimension should be decided according to clean room design, while the inner dimension is for the operation area.
2. The dynamic passbox is suit for the transmission happened from lower cleanliness environment to higher cleanliness environment. If the transmission happens between same cleanliness, static passbox is recommended.
3. The direction of door opening should be considered according to the position of passbox.
4. SUS 304 is recommended for the casing of passbox.
5. If the transfer cart is required in clean room, the floor-mounted passbox is recommended.
Contact Person: Nicole