|Fan:||Aluminum Impeller||Air Velocity:||0.45m/s|
dynamic pass box,
air shower pass box
This dynamic pass box with DOP test port is used for drug research in Australia,it was made from high quality material---SS304,hepa has good efficiency, detailed parameter as bellow:
|material||304 stainless steel|
|open ways||9pcs right open(p: 1,3,5,6,8,12,10,14,16),7pcs left open(p:18.104.22.168.7.13.15) as buyer's shows in PDF|
|Others||add new pipe,change programme,round handle,English control panel,50mm stop and socket,LED lights,as confirmed by emails+one extra free hepa outlet|
Product working process:
1, POWER:220V/50HZ, power ups 1-5s, Light becomes RED, touch display begins working status;
2, Door A:touch door swift on display, light becomes GREEN, power off, B door light turns RED;
3,Put goods inside box, door A closed, light turns RED, fan begins working, two lights turn RED. Clean time is finished, two lights turn GREEN.(open door B, light turns GREEN, door A light turns RED, on the contrary).
4, Door B open, when touch door swift, take out goods, if need fan goes on working at this time, press fan swift, on the contrary.
5, time set up: press 1-3s on time show area, then can set time from 0-99s, advice 30s, then save:
6,how to open stoppers?
A: Press down black ring, then can pull out white stoppers.
B:big stopper is a nut cover, rotate to unscrew:
Note: when Pascal reach 350-400, advice replacement of heap filter( liquid seal heap filter), in China, people replace one time each year or 1.5 yeas!
Customer's feedback :
Customer's using feedback:
Contact Person: Nicole Yu