Mr Bob MccabeWe have purchased 6 sets Roller Shutter Door for our candy factory from your company. Good quality! Good sevice! We will purchased other clean room equipment from your company later.
Mr ManhThis year we are going to build a mobile phone screen electronics clean factory.We send Hongkong YaNing a list of products we need,Unexpectedly, they soon gave me a very detailed quotation and drawings, and gave us a lot of good advice. Very professional, good service, good product quality! We decided to place an order.
High Temperature HEPA Air Filter 15.6㎡ Large Filter Area For Food Factory
|Place of Origin||China|
|Minimum Order Quantity||1 pcs|
|Packaging Details||First in pp bag,then in carton,final made a wooden box. or as your requirement.|
|Delivery Time||7-30 workdays|
|Payment Terms||L/C, T/T, Western Union|
|Product Name||High Temperature Resistance Hepa||Frame Material||304 Stainless Steel|
|Size||630*630*292mm Or Custom||Separate||Aluminium Foil|
|Filter Media||High Temperature Glass Fiber||Air Volume||1500 M³/h|
|Filter Area||15.6㎡||Packaging||Wooden Case|
high efficiency hepa filter,
mini pleat hepa filter
High temperature hepa filters High Temperature Resistance hepa for food factory
·High efficiency(capturing 0.5 or above 0.5μm Particles)
·Large dust holding capacity
·Fine uniformity of air velocity
Features: It can be used as final air filter in some more high efficiency place.. Good permeability, let dust amount is large, stable performance, etc.
Application: Cleaning room in air conditioner system.
It is applied to dead-end filtration of thecleanroom and many kinds of cleaning equipments
Type: high efficiency box filter
Max. air flow: 125% of the rated air flow
Temp resistance: 80ºC
Frame: 304 stainless steel
Media: glass fiber
Sealant: high temperature silicon
Separators: aluminum foil
Humidity resistance: ≤95%RH
Working temperature: ≤250℃
Standard Model Technology Parameter
|Model||Size(mm)(W*H*D)||Rate air flow(m/h)||Initial pressure drop (Pa)||efficiency % 0.3u(DEHS)|
|Note||Deep pleat hepa filter can be customized according to the site.|
Care and maintenance
1. The surface of the Hepa air filter is dark, and when the dust is contained in large quantities, the resistance increases, ie, the non-woven fabric inside the high-efficiency air filter is removed for cleaning, or it is replaced.
2. Regularly check the air velocity of the nozzle at regular intervals (1-2 times a year). If it does not meet the technical requirements, replace the high-efficiency air filter.
3, the replacement should pay attention to the new high efficiency air filter model specifications and the original high-efficiency air filter, high efficiency air filter paper and wood structure, installation should be careful, do not touch the border, damaged filter paper.
4, when replacing a high-efficiency air filter, the nozzle flap must be removed and the high-efficiency air filter removed. Replace with a new high-efficiency air filter. Attention should be paid to the arrow mark on the high-efficiency air filter. The arrow points to the direction of airflow.
5. After replacing the new high efficiency air filter, it must be confirmed that there is no leakage between the filter and the sealing material and the frame supporting the filter.
6. Conduct electrical circuit inspections on a regular basis.